OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00091|
|PWS Name:||AVION WC - GREATER AVION|
|Who Was Contacted and Phone:||Art Sharkey (541) 382-5342|
|Contacted By:||BYRD, MICHELLE P (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||SUMMARY: Routine total coliform positive DETAILS: Received a call from Art on August 13th about distribution sample collected August 12th at Hunnell Rd site being total coliform positive. Follow-up repeat sampling was being done at upstream, downstream and original sites, in addition to source water sampling at wells in use at the time including: Parrell Rd, China Hat wells 1 & 2, Tekampe wells B & C, and Dyer well.
Received a call on August 14th that all follow-up samples were absent. ACTION NEEDED: No further action.
|Associated Alerts:||COLI11949 - 08/14/2013 - COLIFORM (TCR)