|Most Recent Water System Survey|
|Survey Date:||Nov 23, 2021|
|Notification Date:||Dec 15, 2021 (22 days)|
|Regulating Agency:||WASCO COUNTY|
|Survey Frequency:||Visit the Water System Surveys page to see the list of surveys due each year.|
§ A "Failure to Correct Deficiencies" reminder letter was sent to the water system for this deficiency.
* Corrective Action Plan has been submitted for this deficiency.
|Water System Site Visit History|
|Reason||Visit Date||Frequency||Next Due||Notification Date
(Days after survey)
|Sanitary Survey, Finished (SNSV)||11/23/2021||*||12/15/2021 (22)||WASCO COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||12/03/2018||3 YR||*||12/05/2018 (2)||WASCO COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||11/18/2015||3 YR||*||11/23/2015 (5)||WASCO COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||11/14/2012||3 YR||*||11/20/2012 (6)||WASCO COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||09/15/2009||3 YR||*||09/22/2009 (7)||WASCO COUNTY||Hide details|
no screened vent on well casing. no treated water sample tap. - add if going to chlorinate crack in concrete reservoir piping configuration needs investigation to verify there is a drain for the reservoir and it has a flap valve on it and can be taken offline or bypassed. facility map needed for water system. routine flushing of dist is needed. no cross connection annual summary report since 2002 lead and copper needed by end of sept 2009. missing 2quarters of rads need coliform sampling plan need ops and maint manual need emergency response plan need certified operator need written porotocols need consumer confidence reports for 2007 & 2008 rg 12/16/09
This site visit has not been entered into the deficiency database.
|Sanitary Survey, Finished (SNSV)||06/21/2006||3 YR||*||08/08/2006 (48)||WASCO COUNTY||No details|
|Sanitary Survey, Finished (SNSV)||01/17/2002||3 YR||*||WASCO COUNTY||Show details|