OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 06280|
|PWS Name:||211 FARM - WILLAMETTE NURSERIES|
|Advisory Type:||Do Not Drink Water|
|Begin Date:||May 21, 2019|
|Date Lifted:||May 14, 2020|
|Contacted By:||FERGUSON, JOEL (CLACKAMAS COUNTY)|
|Who Was Contacted:||Alex Cooper|
|Details:||During the inventory of the system, it was determined that the .046 arsenic sample was taken at this system. The do not drink was lifted at PWS#4105663 applied to this system. The operator is looking into treatment will go through plan review for the arsenic treatment the owner chooses.
Lifted 05/14/2020: 5/14/20 : System has installed point of use filters after both drinking water fixtures and received final approval with test results for both filters under the arsenic MCL. I discussed with Clackamas County HD today that we approve of the system lifting the do not drink notice. System will continue with the recommended testing of arsenic after the filters for a non-EPA system and follow up with the County for any questions.