OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 05258|
|PWS Name:||SUNSET HILLS DOMESTIC WATER ASSOCIATION|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||Aug 04, 2017|
|Date Lifted:||Sep 05, 2017|
|Contacted By:||HAMBLIN, MAX (EHS)|
|Who Was Contacted:||Keith White|
|Details:||Aug 4th the systems pump went out, causing depressurization. A sample was taken the first week of August and that RT sample came back positive for Total Coliform. They received the call on August 4th. A Boil Water Notice was hand delivered to all customers on the 4th. On Monday, August 7th, a new ell was installed and the water pressure was restored. The cistern was shocked and is now allowing 24hrs to sanitize. Keith is going to take a sample early Tuesday the 9th. If that is clear, then the water will be run through the system to clear the Cl2 and the notice will be lifted.
Keith is going to send in all paper work to the State on or about the 10th.
If the sample comes back positive, the system will move forward with the next steps.
Update 09/05/2017: The system has shocked the system and regained pressure. Follow-up samples on 8-9-17 and 8-10-17 were all negative.
Lifted 09/05/2017: Please lift boil water notice.