OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00862|
|PWS Name:||CROOKED RIVER RANCH WTR CO|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Area Affected:||Partial - 86 people affected in the lower level|
|Begin Date:||Sep 05, 2019|
|Date Lifted:||Sep 07, 2019|
|Contacted By:||BYRD, MICHELLE P (DWP)|
|Who Was Contacted:||Frank Day|
|Details:||Frank notified me on Tuesday Sept. 10th about a waterline break on Thursday, Sept. 5th in the lower part of the distribution system from the store to the northern end of the system. The break occurred around 3:30 pm. resulting in a loss of pressure to 86 customers. These customers were notified via bulk email, auto-dialed message, website and news media. Door to door notification was provided to customers at three RV parks. Frank indicated they would normally go door-to-door but staffing was limited. Repairs were completed on the same day. On Friday, September 6th the affected area was flushed followed by collecting a coliform sample.
Lifted 09/07/2019: The sample collected on Friday, September 6th was coliform absent. The water supplier lifted the boil water advisory notifying customers by auto-dialed message and recommended flushing of premise plumbing.