OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00727|
|PWS Name:||ST PAUL, CITY OF|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||Feb 29, 2020|
|Date Lifted:||Mar 03, 2020|
|Contacted By:||DEBLASE, GREG (MARION COUNTY)|
|Who Was Contacted:||Ben Unger|
|Details:||Ben called on 3/2 to report a power outage on the morning of 2/29. Their new generator was not set to auto so it had to be manually activated. Ben said the loss of pressure lasted about 20 minutes. The system has issued a boil water advisory and notified customers. TC samples were collected on 3/2 and results expected today. The generator is now set to auto mode and is checked regularly.
Lifted 03/03/2020: Ben emailed me the coliform test results from edge analytical. The boil water advisory has been lifted.