OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 95127|
|PWS Name:||SALMON RUN GOLF COURSE|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||May 08, 2020|
|Date Lifted:||Jun 12, 2020|
|Contacted By:||DOWNS, KENT (DWP)|
|Who Was Contacted:||MARK HAGLUND|
|Contact Phone:||541-412-0424 ext 7|
|Details:||Operator posted a boilwater notice on Friday, May 8,2020 due to loss of pressure. The system was taken off-line and connected to a new drilled well. The new well is currently being evaluated and tested. The distributions lines were flushed and the system is espected to be back on-line next week (May 13). On this date the operator plans to test the water quality in the distribution lines to ensure abcense of colifrom bacteria. The boil water advisory will be removed when the distribution water sample test result shows an abscence of coliform bactiera. However, the operator was instructed not to use the new source until a raw water sample is colleted and tested for Arcenic, Nitrate and Coliform Bacteria. Operator was also instrcuted to provide copy of the plan review approval by the DWS Office.
Lifted 06/12/2020: Water system tested for Arsenic, Nitrate and coliform bacteria. Arsenic and Nitrate levels are acceptable. No E. coli or TC found in the distribution sample. New Well (SRC AB) tested absent for E. Coil, but positive for TC. However, the UV reactor is maintaining the minimum 4 log disinfection in the distribution line.
|Associated Alerts:||COLI19923 - 06/12/2020 - COLIFORM (TCR)