OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 01532|
|PWS Name:||VINTAGE RUCKLES WATER|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Jul 09, 2020|
|Date Lifted:||Sep 30, 2021|
|Contacted By:||WIKSTROM, CHANTAL (DWP)|
|Who Was Contacted:||Caroline Gross-Regan|
|Details:||Phone Duty Alert. Routine and repeat samples came back positive for E. coli and this water system issued a boil water advisory for all users last night (7/9). I spoke with Caroline at Douglas County who said the system shock chlorinated and confirmation samples have been sent in to the lab.
Lifted 09/30/2021: Vintage-Ruckles has installed 4-log virus inactivation treatment (sodium hypochlorite injected with a chemical feed pump). The minimum residual is set at 0.2ppm. Routine coliform sampling has been set back to quarterly. Coliform samples taken since the installation have come back clean.