OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00280|
|PWS Name:||CEDARHURST IMPROVEMENT CLUB|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||Sep 16, 2020|
|Date Lifted:||Sep 17, 2020|
|Contacted By:||NUSRALA, JAMES (DWP)|
|Who Was Contacted:||Phil Jones|
|Details:||System was impacted by fire and evacuated on 9/9. System was shut down and positive pressure lost after this evacuation and a boil water notice was distributed to all customers as the evacuation was lifted and people started coming back to system on 9/11. Well and chlorinator currently working. Distribution system comprised of plastic pipes, and given that fire chared a portion of the system, which was de-pressurized, DWS to provide guidance on including VOC sample along with coliform sample to lift no pressure boil notice.
Lifted 09/17/2020: With concerns about structural PVC pipe damage due to burning and loss of pressure, system issued a do not drink notice to all customers initially, Sept 11. DWS to follow up with guidance on potential VOC sampling in distribution.