OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 06045|
|PWS Name:||UPTON TRAILER PARK|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Unconfirmed (Voluntary)|
|Begin Date:||Oct 01, 2020|
|Date Lifted:||Oct 07, 2020|
|Contacted By:||SMITH, LENORE (LANE COUNTY EHS)|
|Who Was Contacted:||Wendy Crymes|
|Details:||As a precautionary measure I recommended a boil water notice be posted until we get results back from repeat samples taken.
Spoke to Wendy and all samples came back absent for E.coli and T.coliform. She didnt have enough sample bottles so she will send in a sample from distribution that wasnt sampled yet and will contact me with results. She posted boil water notice today and emailed me her copy of boil water notice. Will leave boil water notice in place until she contacts me with last sample result and also take 5 confirmation samples at the source.
Lifted 10/07/2020: All 5 confirmation samples and 3 temporary routine samples for October are absent for E.Coli and T. Caliform. Boil water notice lifted and copy emailed to compliance today. Water system is back to quarterly sampling and no other action is necessary.