OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 95626|
|PWS Name:||PFEIFFER WINERY|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Area Affected:||Partial - tasting room hand wash sink.|
|Begin Date:||Oct 14, 2020|
|Date Lifted:||Oct 20, 2020|
|Contacted By:||GREEN, JEFF (DEPT OF AGRICULTURE)|
|Who Was Contacted:||Robin Pfeiffer|
|Details:||Positive E. coli in repeat sample collected at tasting room hand wash sink.
Lifted 10/20/2020: Visited system on 10/16/20. System chlorinated spring box and distribution on 10/13/20. Post chlorination test results were absent for coliform. I tested for residual chlorine at 4 sample locations. Three sample locations were non-detect. One sample location tested 0.2ppm. The system drilled a new well and will be connecting to the well as the new source. The well is currently not approved and requires completion of plan review.
|Associated Alerts:||COLI20420 - 10/14/2020 - COLIFORM (TCR) , E. COLI See also: 10/16/2020, 10/14/2020