OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 90594|
|PWS Name:||NESTUCCA HIGH SCHOOL|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Jan 07, 2021|
|Date Lifted:||Jan 15, 2021|
|Contacted By:||PAMPUSH, ANNETTE (TILLAMOOK COUNTY)|
|Who Was Contacted:||Bill Wilkerson|
|Details:||Bill initially was unsure as to why they got the positive sample. He is a relatively new operator. Follow up samples came back positive as well. He contacted the previous operator and OAWU for asistance. It turns out he did not know there was a springbox and he had taken the sample from a pipe from the pond. He unearthed the springbox and resampled directly from it. all samples negative. he is planning cleanup of the system.
Lifted 01/15/2021: Samples which were taken directly from the springbox all came back negative per verbal from Waterlab.
|Associated Alerts:||COLI20727 - 01/07/2021 - COLIFORM (TCR) , E. COLI See also: 01/07/2021