OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 93944|
|PWS Name:||DOUGLAS CO PKS WHISTLERS BEND|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Aug 09, 2018|
|Date Lifted:||Oct 01, 2018|
|Contacted By:||TEMPLIN, REBECCA (DWP - SPRINGFIELD)|
|Who Was Contacted:||Eddie Montgomery|
|Details:||System is doing a voluntary boil notice because the EC+ results from sample taken 8/8/2018. System was going to check the cartridge filter pressure gauges. System has not changed out the cartridge filter since it was installed (conditional approval was given in October 2017). System is taking necessary follow up samples.
Lifted 10/01/2018: System completed Level 2 investigation and made improvements to new cartridge filter system. System is now recording chlorine residual and turbidity. System also had a clean coliform sample taken on 9/20/2018 so water boil advisory is lifted.
|Associated Alerts:||COLI18073 - 08/10/2018 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 08/10/2018, 08/09/2018