OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00828|
|PWS Name:||INDIAN MEADOW WATER COMPANY|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Aug 11, 2018|
|Date Lifted:||Aug 17, 2018|
|Contacted By:||BYRD, MICHELLE P (DWP)|
|Who Was Contacted:||Lynn Lounsbury/Jeff Freund|
|Details:||Spoke to Jeff Freund on Friday Aug. 10th about E coli positive routine sample collected Aug. 9th. Lynn was notified to collect repeat and triggered source samples. On Saturday Aug. 11th, Jeff notified me that a repeat sample was total coliform positive. Water system was placed on a boil water advisory. Triggered source samples would be collected on Monday Aug. 13th. The water system is taking steps to correct the contaminant issue.
Lifted 08/17/2018: After chlorinating and flushing reservoir and distribution, system took 2 follow up samples from distribution and a source sample from the north well. All results absent for bacteria as of approximately noon 8/17. Spoke with operator Lynn and he will lift boil water advisory and notify users via signs in the neighborhood. A level 2 investigation will be conducted next week. Continue normal routine sampling in September.
|Associated Alerts:||COLI18080 - 08/10/2018 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 08/10/2018