OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 01217|
|PWS Name:||LATOURELL FALLS TOWNSHIP|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed at GW Source Without Treatment|
|Begin Date:||Sep 30, 2021|
|Date Lifted:||Oct 15, 2021|
|Contacted By:||GEORGE, JENIFER (MULTNOMAH COUNTY)|
|Who Was Contacted:||Richard Lowery|
|Details:||Repeat samples resulted in positive for ecoli
5 confirmed samples taken with 4 of samples positive for ecoli.
Went out to water system and found the spring box lid is not watertight and the tap is not adequate.
These are the concerns that should be fixed and then resampling.
Lifted 10/15/2021: 3 samples were taken from the source with results of negative for e-coli. Monthly monitoring will take place.
|Associated Alerts:||COLI21449 - 09/29/2021 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR)