OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01172|
|PWS Name:||WESTERN HILLS MH ESTATES|
|Who Was Contacted:||Robert Trotter|
|Contacted By:||OSBORN, DANIEL (COLUMBIA COUNTY)|
|Details:||I spoke with Robert Trotter about Western Hills MH Estates' Lead and Copper treatment; the 2020 results were above the Action Level which led the system towards treatment requirements. However, this water system already had treatment that could be applied to Lead and Copper; a pH adjustment/soda ash treatment component.
Robert says that up until late 2020 under previous ownership, the pH adjustment/soda ash treatment components allegedly had not been maintained on a routine basis suitable to adjust for pH. Robert says that since then, he tries to ensure the system stays around a pH of 7.2
Robert forwarded to me the most recent Lead and Copper sample results for Western Hills, received on 7/1/22, which were all either non-detect or below the Action Level for Lead and Copper. I forwarded those results to OHA DWS.