OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 95127|
|PWS Name:||SALMON RUN GOLF COURSE|
|Who Was Contacted:||Michael Matheson|
|Contact Phone:||254-212-9645 (Email address hidden)|
|Contacted By:||DOWNS, KENT (CURRY COUNTY)|
|Assistance Type:||INCIDENT RESPONSE|
|Details:||UV System up and running.
I received an email from Mr. Matheson informing me that the UV system is back online. At the direction of the Viqua technician Mr. Matheson and his operators were able to take the faceplate off and change one of the fuses under the housing. This allowed the units to return to 100% capacity. They flushed the lines and collected samples that were sent off to The Lab. The boil water notice will remain in effect until they get confirmation from the lab that the samples are free from Total Coliform and E.coli.