OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94431|
|Who Was Contacted:||Keith Beckman|
|Contact Phone:||-- (Email address hidden)|
|Contacted By:||TEAMUS, JOSHUA (DEPT OF AGRICULTURE)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||On April 29th, JLR took a quarterly sample to test for arsenic. The result (0.0153mg/L) returned above the MCL for arsenic (0.010 mg/L). JLR updated and reposted their public notice around their facility. A copy was received and forwarded to Compliance.DW.
The running annual average (RAA) is below the MCL. (0.007 mg/L)
The system has already installed arsenic treatment. It is thought that the media was exhausted and resulted in arsenic in the water. The system is testing the media and will replace if it is indeed exhausted.
|Associated Alerts:||CHEM8320 - 05/01/2019 - ARSENIC