OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01031|
|PWS Name:||SHADY ACRES MHP, LLC|
|Who Was Contacted:||Dan Perkins|
|Contacted By:||WRAY, JULIE (DWP)|
|Assistance Type:||CIRCUIT RIDER ASSISTANCE|
|Details:||Shady Acres mobile home park water system was tested for lead and copper content and it was found to have exceed the lead action level (AL) of 0.015 mg/L. The results were received by the state on September 26th, 2018 and notice of exceeding the AL was given to the water system on October 15st, 2018. Part of the requirement of this notice was that the water system needed to receive a recommendation from a water system engineer for an optimal corrosion control treatment.
After researching the system and the constituents of their source water it was determined that adding soda ash to the source water would be the most effective method of controlling corrosion throughout the water system. Soda ash can be added shortly after the well head using an off the shelf soda ash package similar to the J-PRO-22+15. Before implementing a system, a more thorough analysis of the water should be performed.
Memo to Dan on March 27th, 2019.