OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94934|
|PWS Name:||SEA CREST MOTEL|
|Who Was Contacted:||Jeremiah Nelson|
|Contact Phone:||541-655-0198 (Email address hidden)|
|Contacted By:||DOWNS, KENT (CURRY COUNTY)|
|Assistance Type:||OTHER REGULATORY - L2 Investigation completed|
|Details:||L2 Investigation Completed.
Corrective actions completed on 07.27.2019
1. Cross connection between the old hand dug well and the concrete reservoir for Sea Crest Motel found. Operator made a line break, disconnecting the hand dug well and the neighbor’s service line from the Sea Crest water system.
2. pump house and area around the sampling tap cleaned. Works to reposition raw water sample tap for well L34043 will be completed on 08.12.19.
3. Screen mesh installed on the pipe protruding from the concrete reservoir.
4. Reconstructed the access hatch for the concrete reservoir.
5. Replaced screens in the pump house and sealed up holes in the pump house to prevent the entrance of rodents and other critters.
|Associated Alerts:||COLI19043 - 07/19/2019 - COLIFORM, TOTAL (TCR)
|Associated Violations:||Viol #900732625, 07/01/2019 - 07/31/2019: TCR - Acute MCL for E. coli