OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01399|
|PWS Name:||LAZY ACRES MOBILE HOME PARK|
|Who Was Contacted:||Mike Lowrie|
|Contacted By:||DEBLASE, GREG (MARION COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||I called Mike and he was aware of the arsenic detection of 0.011 mg/l. He said he just added new filter media earlier this year. He will be going onsite to investigate and will follow up with me with any findings next week. I let him know the monitoring schedule will remain on quarterly.
Mike called me back to report that the treatment was accidentally left in by-pass. He said he is going to collect another sample. I reminded him that a bypass valve is not allowed for arsenic treatment unless it is physically separated (such as a pipe spool) as valves can leak or fail.
|Associated Alerts:||CHEM8507 - 09/13/2019 - ARSENIC