OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01182|
|PWS Name:||COUNTRY GARDEN ESTATES MHP|
|Who Was Contacted:||Howard Marbut|
|Contact Phone:||541-922-4614 (Email address hidden)|
|Contacted By:||WORD, AMY (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||The water system had collected a monthly routine sample on 6/9/20. The system said there was a free chlorine residual of 0.4. An on-site visit/water system survey was done on 6/19/20. Three repeat samples and one triggered source sample were collected. All were absent for bacteria. The survey done on 6/19/20 showed the chlorine test kit being used was not measuring free chlorine. So, the free chlorine readings written down were incorrect. Measurements taken during the survey showed 0-0.1 (trace) amounts of free chlorine.
Extra free chlorine test packets were left with the water system. Resource links for replacement packets and other test kit were sent by email to Howard and Kathy.
|Associated Alerts:||COLI19915 - 06/11/2020 - COLIFORM, TOTAL (TCR)