OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00233|
|PWS Name:||CROOKED CREEK TRAILER PARK|
|Who Was Contacted:||Manfred Doerner|
|Contacted By:||KRUGER, SCOTT (BENTON COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||I received a text from Rudy Doerner that the water system tested positive for E-coli on 7/18/20. After speaking to his father Manfred on 7/20/20 I discovered that the routine test result was Coliform positive not E-coli. Manfred stated that he had already shock chlorinated the water system and posted a Boil Water Notice out of abundance of precaution.
I instructed Manfred to flush the water system to remove excess chlorine. The system is chlorinated. Manfred stated that a feed tube on the chlorinator was broken and was not feeding chlorine to the system. He was advised to submit three repeat distribution samples and a triggered source sample. He was advised that if the repeat samples returned positive that a Level 1 investigation would be required.
|Associated Alerts:||COLI20066 - 07/20/2020 - COLIFORM, TOTAL (TCR)