OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 05364|
|PWS Name:||MT TERRACE MHP|
|Who Was Contacted:||craig bennett|
|Contact Phone:||-- (Email address hidden)|
|Contacted By:||HALLMARK, RICK (COOS COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||As follow-up to (1)the ALERT relating to arsenic results of 0.0148 (above the MCL) sample taken 6/21/18 and (2) unconfirmed corrections of deficiencies from the 2017 survey this email was sent:
Craig: things to cover in this message:
1. Update and distribute the arsenic public notice to your tenants. Send a copy of that notice to me or the state (or both).
2. As long as well #3 continues in use, without effective treatment, quarterly arsenic sampling is a requirement.
3. Follow what the state guys tell you to do in order to have [plan review] approval to use a new well and/or provide treatment for arsenic removal. Pay especial attention to any dates/deadlines.
4. As per your message below: Your responses to (2) and (4) sound satisfactory. Your responses to (1) and (3) need clarification. I have attached what might help you prepare an (1) Emergency Response Plan and the following link might help you prepare an (3) Operations and Maintenance Manual: http://www.nesc.wvu.edu/pdf/dw/publications/ontap/magazine/OT_WI10.pdf#page=27 The simplest O and M will have a list of prudent activities with a schedule to complete and a "how to" section for use of equipment and any technical operation activities.
A separate email was sent including 3 attachments relating to doing a security and vulnerability assessment and preparing an emergency response plan.
Craig Bennett forwarded the public notice to me on 7/7/18 and replied to my email directly on 7/9/18.
|Associated Alerts:||CHEM7973 - 06/27/2018 - ARSENIC