OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 05998|
|PWS Name:||WESTRIDGE SUBDIVISION|
|Who Was Contacted:||Wayne Looney|
|Contact Phone:||541-416-9380 (Email address hidden)|
|Contacted By:||BYRD, MICHELLE P (DWP)|
|Assistance Type:||OTHER REGULATORY - 4-log disinfection verification|
|Details:||On December 2nd, I received an email from Wayne that on December 1st Westridge completed the modifications to the water system as required in the BCA. The farmhouse next to the well and chlorination building was disconnected from the water system and is now served by the new well. All other customers are being served by the original well as per accepted plan since this well after further evaluation met the construction standards. Information to verify 4-log disinfection for the water system was emailed.
On December 18th, I spoke to Wayne and he verified the 4-log disinfection information previously sent as correct. Proceeded to established a minimum chlorine residual of 0.4 mg/L at the first user (EP-A). As of January 1, 2021, the water system will start daily reporting of chlorine residual and report data monthly to the state.