OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 95127|
|PWS Name:||SALMON RUN GOLF COURSE|
|Who Was Contacted:||Mark Haglund|
|Contact Phone:||-- (Email address hidden)|
|Contacted By:||DOWNS, KENT (CURRY COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||The water system operator has decided to post a boil water advisory until test results for a sepcial sample collected in the distribution lines can confirm absence of E. Coli contamination.
Water from the well is first treated with a Viqua Pro 24-186 UV reactor for disinfection. The operator reported that their UV reactor has been working properly. A boil water advisory is not a requirement if the system was meeting 4.0 log inactivation at the time they were confirmed and a few days before. Likeways, there is currently no requirement to post a boil water notice if their UV was working property and was applying at least 186 mj/cm2. This information was shared with the operator.
A copy of the boil water advisory posted at Salmon Run Golf Course was emailed to DWS. The advisory will be removed once test results confirm absense of contamination with E. Coli in the distribution lines.
|Associated Alerts:||COLI20700 - 12/28/2020 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 12/29/2020
COLI20677 - 12/21/2020 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 12/21/2020, 12/29/2020