OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 91209|
|PWS Name:||CURRY CO PKS LOBSTER CREEK|
|Who Was Contacted:||Anthony Derock|
|Contact Phone:||541-247-3386 (Email address hidden)|
|Contacted By:||DOWNS, KENT (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||04.13.21 - Anthony informed me that the park is currently closed. Follow up confirmation samples will be collected on 04.14.21. No temporary source of contamination observed in the well. We discussed updating the coliform sampling schedule. I emailed Anthony a copy of the coliform sampling plan template to update the one they have with the current RT sample sites.
The existing raw water sampling tap is too close to the grown and also too close to the wall surrounding the wellhead. To prevent cross contaminating the raw water sample, the operator will collect raw water samples at the raw water line entering the storage tank.
|Associated Alerts:||COLI20908 - 04/12/2021 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR)
COLI20909 - 04/12/2021 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR)