OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01058|
|PWS Name:||SEVENTH MOUNTAIN RESORT|
|Who Was Contacted:||Bryan Ricci|
|Contacted By:||FREUND, JEFF (DESCHUTES COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||Two samples taken in response to positive samples at the Arrowood system which Seventh Mtn. is the wholesaler. Samples were labeled repeats, but sdwis only accepted them as routines. Samples were from the maintenance shop (first sample point out of reservoir) and the drinking fountain (questionable sampling site). 2 of four repeat samples in Arrowood also positive. 7/14 routine sample from maintenance shop absent.
Arrowood on a boil notice since 7/16 for confirmed e.coli in distribution. Both systems share a reservoir. Plan is to flush both systems and resample Friday. If coliforms still present, they will chlorine reservoir to 10 mg/L, flush, ensure 0 chlorine and take additional samples.
Seventh Mtn. will need to take 3 temporary routine samples in August due to two positives in July.
|Associated Alerts:||COLI21192 - 07/22/2021 - COLIFORM, TOTAL (TCR)