OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94205|
|PWS Name:||COE PHILIPPI PARK|
|Who Was Contacted:||Monica Carter|
|Contact Phone:||-- (Email address hidden)|
|Contacted By:||GRENDEL, ERIC (WASCO COUNTY)|
|Assistance Type:||OTHER REGULATORY - Loss of Pressure|
|Details:||I received an email from Monica about scheduling our level 2 investigation for the current boil water advisory. In communicating with her, she mentioned that her crew was currently working on a broken water line and loss of pressure. She wanted to know if that would impact the level 2 investigation. I let her know that it wouldn't however she would need to update the boil water notice with information regarding the loss of pressure and she would need to correct the issue, flush the system and hook up disinfection before drawing a sample for validation. I told her that she could use the sample as a routine sample, as she has not submitted for the month of August yet.
The line that was broken was an irrigation line and did not impact the drinking water line at all. Will move to lift the boil water advisory as the repeat samples were absent of coliforms. Corrective actions taken were flushing, chlorinating and turning the UV treatment back on.