OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01450|
|PWS Name:||UNITY, CITY OF|
|Who Was Contacted:||Ken Taylor|
|Contacted By:||WORD, AMY (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||The water system (since May) has been collecting two routine coliform samples per month (from the same location). Both samples that were collected on 9/8/21 came back positive for total coliform bacteria. Three repeat samples and one triggered source sample were collected on 9/15/21. One of the repeats (different location) was present for coliform. The other samples were absent for coliform bacteria.
Only two wells have been active since June (SRC-AA and AB). The ranger station well (SRC-AC) has not been used.
I asked the system to take a SRC-AB sample with their routine October sample. Due to the system layout, a common-header source sample request (ARC-AA and AB) will be evaluated.
|Associated Alerts:||COLI21404 - 09/20/2021 - COLIFORM (TCR)
COLI21375 - 09/10/2021 - COLIFORM (TCR)