OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00091|
|PWS Name:||AVION WC - GREATER AVION|
|Who Was Contacted and Phone:||Gene Hubbard (541) 382-5342|
|Contacted By:||BYRD, MICHELLE P (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||SUMMARY: Routine total coliform positive DETAILS: Received email from Gene of a routine total coliform positive sample collected on January 12th at the Bear Creek Sample Station. Both Parrel Rd. (SRC-HA) and China Hat 2 (SRC-AB) were in use at the time. Repeats and triggered source samples are being collected. He noted inclement weather has been problematic for sampling and maintaining operations.
Received email on January 17th from Gene that all follow-up samples collected the previous day were coliform absent. ACTION NEEDED: No further action at this time.
|Associated Alerts:||COLI16491 - 01/18/2017 - COLIFORM, TOTAL (TCR)