|Introduction :: Data Search Options :: WS Name Look Up :: WS ID Look Up :: DWS Home :: DWS Rules :: Quick Data Links|
|Most Recent Water System Survey|
|Survey Date:||Nov 30, 2017|
|Notification Date:||Dec 11, 2017 (11 days)|
|Regulating Agency:||POLK COUNTY|
|Survey Frequency:||3 YR - Visit the Water System Surveys page to see the list of surveys due each year.|
No deficiencies were identified.
|Water System Site Visit History|
|Reason||Visit Date||Frequency||Next Due||Notification Date
(Days after survey)
|Sanitary Survey, Finished (SNSV)||11/30/2017||3 YR||*||12/11/2017 (11)||POLK COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||09/25/2014||3 YR||*||09/13/2014 (-12)||REGION 1||Show details|
|Sanitary Survey, Finished (SNSV)||05/21/2010||3 YR||*||06/17/2010 (27)||DWP||Hide details|
Deficiencies noted include: 1. Sanitary seal and casing not water tight on well. 2. Chlorine not measured and recorded as required. 3. No means to adequately determine disinfection contact time under peak flow and minimum storage conditions. 4. No flap valve, screen or equivalent on drain. 5. No coliform sampling plan. 6. No operations and maintenance manual. 7. Emergency response plan not completed.
This site visit has not been entered into the deficiency database.
|Water Treatment Plant Site Visit (TRTP)||05/21/2010||DWP||No details|
|Water Treatment Plant Site Visit (TRTP)||07/10/2008||3 YR||07/10/2011||07/30/2008 (20)||DWP||Show details|
|Sanitary Survey, Finished (SNSV)||02/14/2007||3 YR||*||10/19/2007 (247)||DWP||No details|
|Sanitary Survey, Finished (SNSV)||10/16/2003||5 YR||*||DWP||Show details|