Resource id #5
|Introduction :: Data Search Options :: Water System Search :: DWS Home :: DWS Rules :: Quick Data Links|
|Most Recent Water System Survey|
|Survey Date:||Apr 13, 2016|
|Notification Date:||May 09, 2016 (26 days)|
|Regulating Agency:||LANE COUNTY|
|Survey Frequency:||5 YR - Visit the Water System Surveys page to see the list of surveys due each year.|
|Water System Site Visit History|
|Reason||Visit Date||Frequency||Next Due||Notification Date
(Days after survey)
|Sanitary Survey, Finished (SNSV)||04/13/2016||5 YR||*||05/09/2016 (26)||LANE COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||10/11/2011||5 YR||*||11/23/2011 (43)||LANE COUNTY||Show details|
|Sanitary Survey, Finished (SNSV)||02/06/2007||5 YR||*||03/26/2007 (48)||REGION 2||Hide details|
signifigant dificiencies are sanitary seal not water tight, no sample tap, no pump-to-waste piping. No screened vent or flap valve on storage tank. NO inorganics test done, no plan review completed for 1994 well. no erp.
This site visit has not been entered into the deficiency database.
|Sanitary Survey, Finished (SNSV)||12/07/2000||5 YR||*||DWP||Show details|