OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 91692|
|PWS Name:||SWEET HOME CHARTER SCHOOL|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Unconfirmed (Voluntary)|
|Begin Date:||Jun 14, 2022|
|Date Lifted:||Jun 17, 2022|
|Contacted By:||KOPPUZHA, DERRICK (LINN COUNTY)|
|Who Was Contacted:||Audrey Richards|
|Details:||Principal of the school was able to post boil water notice around the school while the 5 additional confirmation source samples is being collected and tested. The system does have treatment (chlorination) but is not on 4-log. Chlorine residuals are inconsistent and occasionally below 0.2.
6/15/2022 - School has posted a recommended boil water notice around the building to be on the safe side. Also they have taken the 5 confirmation source sampling - waiting for results.
6/17/2022 - The 5 source samples came back negative for E coli but some were positive for total coliform. Boil water notice can be lifted.
Lifted 06/17/2022: Samples came back negative for E Coli. lifting advisory
|Associated Alerts:||COLI22183 - 06/14/2022 - COLIFORM (TCR) , E. COLI See also: 06/14/2022