OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00872|
|PWS Name:||PINEWOOD MOBILE MANOR|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||Sep 01, 2022|
|Date Lifted:||Sep 09, 2022|
|Contacted By:||GRENDEL, ERIC (WASCO COUNTY)|
|Who Was Contacted:||Jane Ranslam|
|Details:||A trailer at Pinewood Mobile Manor required maintenance on their water line. The valve was not functional and therefore the plumber had to shut off the main water line, losing pressure to the rest of the park. During the repairs, the plumber found that they would also need to fix the main line shut off valve. They will be submitting special samples on Tuesday after the repairs. Customers were notified door to door.
Update 09/07/2022: Special sample came back positive for E. Coli. Boil water advisory will stay in place until shock chlorinating the system and samples come back absent for all coliforms.
Lifted 09/09/2022: Repairs were completed on Tuesday 9/6/22. Lifting boil water advisory after a special sample came back negative for coliforms today.