OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00601|
|PWS Name:||HILAND WC - RIVERBEND|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Jun 16, 2018|
|Date Lifted:||Jun 21, 2018|
|Contacted By:||CHAPMAN, AMY (LINCOLN COUNTY)|
|Who Was Contacted:||Matt Olson|
|Details:||Routine Sample taken 6/12/2018 positive for E. coli.
6/15/2018 took 1 source water sample positive for total coliform only.
6/15/2018 took 3 repeat samples and all were positive for E. coli
Storage tank was chlorinated. Chlorination system is being installed.
Will be re-sampling to be sure there is no coliform bacteria.
Lifted 06/21/2018: Chlorination has been added and subsequent samples are clean. OK to lift the Boil Water Advisory.
|Associated Alerts:||COLI17879 - 06/14/2018 - COLIFORM (TCR) , E. COLI See also: 06/14/2018
COLI17889 - 06/18/2018 - COLIFORM (TCR) , E. COLI