OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00002|
|PWS Name:||ADRIAN, CITY OF|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Nov 13, 2017|
|Date Lifted:||Nov 17, 2017|
|Contacted By:||WORD, AMY (DWP - PENDLETON)|
|Who Was Contacted:||Shawn Snyder|
|Details:||System had a single E. coli sample result received 11/10/17. The on-call DWS manager was Joe Carlson. He discussed the result with the operator and they decided to issue a boil as repeat samples would not be able to be collected until Monday 11/13/17. The water system did issue the boil notice (on 11/13/17) and a copy of the notice was sent to DWS. The system mailed follow up samples to the lab on 11/13/17. Results will not be available till later in the week.
11/16/17 system had collected 4 distribution samples and a source sample on 11/13/17. The source was absent for bacteria and 2 of the distribution were E. coli positive. System has turned up the chlorination and has been inspecting the storage tank.
Lifted 11/17/2017: The water system collected 4 samples on Thursday. The sample results were received on Friday 11/17/17. They were all absent for bacteria. The boil notice has been lifted.
|Associated Alerts:||COLI17427 - 11/13/2017 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR)