OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00174|
|PWS Name:||KNOLL TERRACE PARK|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Begin Date:||Mar 23, 2021|
|Date Lifted:||Mar 26, 2021|
|Contacted By:||KRUGER, SCOTT (BENTON COUNTY)|
|Who Was Contacted:||Taylor Anderson|
|Details:||I received a complaint from a resident in the park due to a loss of pressure and then shortly after a report from the park manager. They were digging a trench and broke a shallow water line. Isolation values are being installed to limit the number of residents affected. A new third party management company will be taking water system operations.
The pressure has been restored, a boil water notice issued. I requested three follow tests in the upper middle and lower sections of the system to verify it has free from coliform.
Lifted 03/26/2021: Three follow -up tests were submitted after the total loss of pressure on 3/23/21. All tests are absent for bacteria. The advisory has been lifted.