OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94489|
|PWS Name:||WHALESHEAD RV PARK & RESORT|
|Who Was Contacted:||Corinne Schrode|
|Contact Phone:||541-469-7446 (Email address hidden)|
|Contacted By:||DOWNS, KENT (DWP)|
|Assistance Type:||SURVEY/DEFICIENCY FOLLOW-UP|
|Details:||Survey deficiency updates.
Corinne and Michelle informed me that the system fixed the issue with the filter effluent turbidity sample tap. She will be down at Whaleshead on Sept 20, to verify the issue was corrected. Corinne was reminded that the water system has until September 20, to update the ERP and the Maintenance and Operation Manual.
Corinne notified me that the following corrective actions have been completed:
- Turbidimeter replaced on 07.10.2022
- Pressure gauges replaced on 07.08.2022
- Operator protocol completed on 07.07.2022. PDF copy provided for verification.
Survey deficiencies still pending:
- Update Operation and Maintenance Manual with SOPs
- Complete Emergency Response Plan
- Filter effluent turbidity not measured prior to storage.