OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00174|
|PWS Name:||KNOLL TERRACE PARK|
|Who Was Contacted:||Sandra Farnham|
|Contact Phone:||541-752-2225 (Email address hidden)|
|Contacted By:||KRUGER, SCOTT (BENTON COUNTY)|
|Assistance Type:||INCIDENT RESPONSE|
|Details:||The operator reported at approximately 9 am on 6/1/23 that there was a planned outage to repair a valve leak adjacent to space 14. The repair required a total loss of pressure to the system. The valve was repaired and the system pressurized at approximately 11 am on 6/1/23.Three follow-up samples were submitted the afternoon of 6/1/23 from the lower, middle and upper sections of the park.
Edge Analytical Lab reports on 6/2/23 at 2 pm that the test results are absent for bacteria.
The operator was notified and the boil water advisory has been lifted.