OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00061|
|PWS Name:||KNAPPA WATER ASSOCIATION|
|Who Was Contacted:||Chris Jackson|
|Contacted By:||REILEY, MEREDITH (CLATSOP COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||Spoke with Chris Jackson, who described action taken after TC+ source samples in October and November: The source well affected has been offline since August. Upon second TC+, the well was chlorine shocked and flushed. Once the residual was back within normal range, a repeat sample was sent to Alexin lab for TC.
Informed Chris that no further repeat samples for the affected well are required--just continue routine (November) sampling elsewhere in system as scheduled.
|Associated Alerts:||COLI19495 - 11/07/2019 - COLIFORM, TOTAL (TCR)
COLI19432 - 10/17/2019 - COLIFORM, TOTAL (TCR)