OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 91036|
|PWS Name:||OPRD COVE PARK-DESCHUTES|
|Who Was Contacted:||Todd Honeywell|
|Contact Phone:||541-546-2862 ext 255 (Email address hidden)|
|Contacted By:||HAMBLIN, MAX (JEFFERSON COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||I visited Cove Palisades - Deschutes Campground today and met with Todd Honeywell, Park Manager.
On 7-28-2020, a source assessment on Well #1 was positive for E. coli. Well #2 was positive for total coliform.
The confirmation samples taken on 7-31-2020 resulted in Well #1 positive for E.coli and Well #2 was positive for total coliform.
In 2012, the system had the same situation and went on a 4-log disinfection course. So on 7-5-2020, this system will start 4-log verification. They are instructed to keep a minimal PPM of 0.5ppm Cl2.
Future communication will result in a time-frame for the recording of the residuals.
|Associated Alerts:||COLI20109 - 08/04/2020 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR)