OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 05690|
|PWS Name:||BANDON BY THE SEA RV|
|Who Was Contacted:||Bob Bryson|
|Contacted By:||HALLMARK, RICK (COOS COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||6/25/21. Bob called to report presence of total coliform found in repeat samples and source sample collected on 6/23/21.
We discussed shocking the well, lines to tank, tanks and lines through affected parts of the RV park followed by flushing prior to collecting temporary routine samples in July.
7/6/21. Bob called to report the well drilling company had helped him with at least some of the system's shock chlorination and in the process of shocking the well thought the seal was in poor condition and replaced it. Bob was hopeful this would resolve the source of contamination.
Tenants were notified of the shock process. Bob expected the system to be flushed clean of chlorine by the week of 7/12 and would collect the 3 temporary routine samples in that week.
|Associated Alerts:||COLI21071 - 06/30/2021 - COLIFORM, TOTAL (TCR) See also: 08/03/2021
COLI21057 - 06/25/2021 - COLIFORM, TOTAL (TCR) See also: 08/03/2021