OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01062|
|PWS Name:||RAINBOW ROCK VILLAGE MHP|
|Who Was Contacted:||Brenda Vasquez|
|Contact Phone:||541-254-1909 (Email address hidden)|
|Contacted By:||DOWNS, KENT (DWP)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||11.12.21 - Brenda was notified by the lab that their RT sample collected in November tested positive for E. Coli and TC. Brenda believes the water sample was contaminated during sampling. It was raining and the torch was not working very well when she tried to heat the tap. Everything else in the water system seemed okay. Repeat samples will be collected on 11.15.21.
The system is maintaining a chlorine residual above 1.0 ppm leaving the plant and has tested free chlorine levels to be well above 0.2 throughout the distribution. There has been no issues with the turbidity. Brenda also reported that they were able to received a new container of coagulant. A jar test was done to adjust the dose of coagulant.
|Associated Alerts:||COLI21659 - 11/15/2021 - COLIFORM (TCR) , E. COLI