OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 00594|
|PWS Name:||CLACKAMAS RIVER WATER - CLAIRMONT|
|Advisory Type:||Boil Water|
|Reason:||Loss of Pressure|
|Area Affected:||Partial - 41 connections on South Sandalwood Rd. and Lora Court, Oregon City, OR|
|Begin Date:||Jun 22, 2022|
|Date Lifted:||Jun 23, 2022|
|Contacted By:||MALE, KEITH (DWP)|
|Who Was Contacted:||Rob Cummings|
|Details:||A repair of a main on South Sandlewood Rd was done under pressure, but when the repair band was installed, the partially closed valve being operated closed and sealed. This resulted in pressure being reduced to 41 connections for up to 25 minutes. The main was flushed for 2 hours and boil notices were posted. Coliform samples were processed at 10:47 pm and will be read today at 4:17 pm today.
Lifted 06/23/2022: The coliform samples collected came back negative the evening of 6/23/2022. The boil was then lifted.