OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 01081|
|PWS Name:||USFS BEAR SPRINGS RS|
|Who Was Contacted:||Jim Belliveau|
|Contact Phone:||508-215-6110 (Email address hidden)|
|Contacted By:||BAILEY, NICOLE (WASCO COUNTY)|
|Assistance Type:||OTHER REGULATORY - Follow up from previous season|
|Details:||Jim Belliveau called to connect with me about Bear Springs Water system. The Bear Springs camp has been closed since Labor Day weekend of 2020 (September) due to previous seasons white river fire.
For the season coming up planned to start April 2, Jim has anticipated improvements to the system to continue the work on the deficiency's noted from last summers level 2 investigation. The chlorinator which was the main deficiency is still working effectively, but there are cleanings and structural improvements to the reservoir that will supplement negating any risk to where e-coli might have been introduced to the system.
I provided Jim VOC and wildfire sampling guidance and he will follow up with me in March
|Associated Alerts:||COLI19957 - 06/19/2020 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 06/30/2020, 07/01/2020, 07/01/2020, 07/06/2020, 07/10/2020, 06/19/2020, 07/13/2020, 07/17/2020, 07/30/2020
|Associated Violations:||Viol #903393322, 06/15/2020 - : TCR - Acute MCL for E. coli See also: 08/27/2020, 07/30/2020, 07/27/2020, 07/17/2020, 07/13/2020, 07/10/2020, 07/06/2020