OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94205|
|PWS Name:||COE PHILIPPI PARK|
|Who Was Contacted:||Monica Carter|
|Contact Phone:||541-739-1128 (Email address hidden)|
|Contacted By:||GRENDEL, ERIC (WASCO COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||Monica sent me an email with the repeat sample results for the system. There was some confusion with the triggered sample and repeat samples that needed to be submitted for the TC+ samples from July 13th. Only 1 repeat sample was considered for the repeat samples and unfortunately it was positive for E.Coli in Dist-A. I sent Monica a boil water notice template and asked for the completed document for our records. Also a level 2 investigation will be conducted.
Received an email from Monica explaining their approach to shocking the system and disinfecting distribution. She mentioned submitting the sample as a "special sample," in which I encouraged her to change to a repeat sample as special samples are technically not considered compliance samples. I gave some advice in disinfecting the sample taps and to ensure that all chlorine was flushed from the system before collecting the samples.
|Associated Alerts:||COLI21175 - 07/20/2021 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 08/31/2021