OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00261|
|PWS Name:||DUFUR, CITY OF|
|Who Was Contacted:||Brandon Beachamp|
|Contact Phone:||541-506-2753 (Email address hidden)|
|Contacted By:||BAILEY, NICOLE (WASCO COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||Called Brandon to request an update on if he recieved the results from the coliform samples he took yesterday.
He flushed the system (5 hydrants) and worked to get a chlorine residual of 0.4 throughout the system yesterday before sampling. He was struggling to get higher than 0.22 ppm in the more stagnant locations of the system but performed a lot of flushing to mitigate any e-coli in the system.
The sample results should arrive to him around 4pm today to decide if the boil water notice can be lowered.
I told him we will need to schedule a lv 2 investigation later this month after things settle with the boil water notice to make a site visit.
|Associated Alerts:||COLI21598 - 11/01/2021 - COLIFORM (TCR) , E. COLI See also: 11/01/2021, 11/02/2021, 11/08/2021
COLI21581 - 10/28/2021 - COLIFORM (TCR) See also: 10/28/2021