OHA Drinking Water Services
Water Advisory Details
|PWS ID:||OR41 94523|
|PWS Name:||CORVALLIS MARKET|
|Advisory Type:||Boil Water|
|Reason:||E. coli, Confirmed in Distribution|
|Begin Date:||Jan 20, 2022|
|Date Lifted:||Feb 14, 2022|
|Contacted By:||HAWKINS, BRIAN (DEPT OF AGRICULTURE)|
|Who Was Contacted:||KULWINDER SINGH|
|Details:||Coliform was present in routine distribution sample taken on 1/12/2022, received 1/14/2022. E.coli bacteria was confirmed in a distribution repeat sample taken on 1/19/2022 and received 1/20/2022. ODA was notified of the confirmed sample on 1/20/2022 and firm was placed on a boil water notice. An on site visit was done 1/21/22 to verify the Boil Notice and a level 2 investigation was completed.
Lifted 02/14/2022: The operator had the well shock chlorinated 1/27/22. The UV light also needed a new fuse and bulb. An absent distribution sample was done 1/31/22 and an absent source sample was taken 2/11/22.
|Associated Alerts:||COLI21879 - 01/14/2022 - COLIFORM, TOTAL (TCR) See also: 01/19/2022
COLI21890 - 01/20/2022 - COLIFORM, E. COLI , COLIFORM, TOTAL (TCR) See also: 02/10/2022, 01/20/2022