OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 00982|
|PWS Name:||DEER ISLAND VILLAGE MHP|
|Who Was Contacted:||Allison, Blueflag Realty|
|Contacted By:||OSBORN, DANIEL (COLUMBIA COUNTY)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||I received a call from Allison with Blueflag Realty, the property management company for Deer Island Village MHP. Allison asked me for specifics about the sampling requirements in response to Well #1's e. coli positive result and the system's Boil Water Notice.
I stated that 5 confirmation samples at Well #1, and at least 1 distribution sample, labeled "special", are required. I also added that the State and I are requesting that a "assessment" source sample also be re-collected at Well #2, prior to any treatment/chlorination, as the original Well #2 assessment sample had a chlorine residual, and therefore may not have been collected at the raw source pre-treatment tap.
Allison said that they are taking care of the sampling, and obtained the proper bottles; she added that someone is planning to go to collect the samples and deliver them to the lab today.
I added that when all those samples test negative for total coliform (and e. coli, obviously), then Deer Island Village MHP may lift their Boil Water Notice.
|Associated Alerts:||COLI22130 - 05/24/2022 - COLIFORM (TCR) , E. COLI See also: 05/24/2022, 05/25/2022, 05/25/2022, 05/25/2022, 05/26/2022, 05/26/2022